REHVA Journal – February 2012
University of Ljubljana
University of Ljubljana
An energy analysis of the complex heating system for heating of buildings, consisting of solar collectors (SC), latent heat storage tank (LHS) and heat pump (HP) was performed. The analysis was made for the heating season within the time from October to March for different climatic conditions. These climatic conditions were defined using test reference years (TRL) for cities: Ljubljana, London, Rome and Stockholm. The energy analysis was performed using a program which allowed hourly dynamics calculation of losses and gains for a given system. It was found that the system could cover more than 50% of energy from the sun and the heat pump coefficient of performance (COP) reached 6.
Buildings share of total energy consumption
is estimated of about 40%. The buildings sector is increasing and this
consequently also increases energy consumption. Because of this reason a
reduction of energy consumption and use of energy from renewable sources
represent important steps towards reduction of greenhouse gas emissions.
Measures to reduce energy consumption could be the increased use of energy from
renewable energy sources respecting the Kyoto Protocol and to meet both
long-term commitment to maintain the global temperature rise below 2°C as well
as a commitment that by 2020 total greenhouse gas emissions must be lower at
least 20% and meet the
requirements of the EPBD 2010/31/EU .
energy consumption and increased use of energy from renewable energy sources
play an important role in promoting security of energy
supply. One of the promising alternatives for heating is solar energy. The best
way to store solar energy is heat storage device.
storage in tanks can be integrated into various systems. One way is the integration in a heating system. A combination of tank and
combustion of biomass gives an optimal performance because the heat which is
not used for building heating is stored in heat storage and can be used for heating
when the heating device does not work .
principles for sensible heat storage device, which is integrated into the
heating system, are purposed by Viorel Badescu . He
presented two models. The results show that the smaller heat storage devices
cool faster than larger ones and that the thermal energy stored per month and
monthly energy used to drive the heat pump compressor increases with increasing
length of the tank. Of course it is possible to integrate the storage device
into the building. In this case heat storage device can have three working
modes: charging with heat, heat discharging (while emptying) and contemporary
charging and discharging. Such heat storage device with alcohol as working
medium in termosifone
gives the best results .
The media, used for filling heat storages devices are different. One
possible medium for heat storing are substances that change the physical state
(Phase Change Materials - PCM), which can be used in different systems for both
heating and cooling. They are very successful in reducing the energy
requirements of buildings . Unfortunately, before their widespread use is
necessary to solve many problems on research and development level. Above all a
lot of attention must be paid to thermal characteristics of PCM .
storage is becoming increasingly important. The use of latent heat storage in buildings has some advantages. By using the proper PCM and its
proper installation latent heat storage devices can be economically efficient
in heating and cooling of buildings. For mass use, it is necessary to solve
some problems of reliability and practicality . Over the past twenty years
PCM and energy storage has been and important subject for research. Review of
publications on thermal energy storage using a solid-liquid phase change was made by Zalba
and other authors .
Energy storage can be carried out according
to the melting/solidification characteristics of PCM. For the base three
different types of paraffin with different melting temperatures were taken. The
impact of Reynolds and Stefan number on melting and solidification of PCM was
determined . In analysing the behaviour of PCM - paraffin in capsules was found
that the phase change occurs in the temperature interval. Use of enthalpy
method showed that the melting process depends mainly on the size of the
Stefan’s number, the temperature at which phase change occurs and the diameters
of capsules . Latent heat storage devices can be used in heating systems
together with solar collectors and heat pump. Simulation was performed for the
system with latent heat storage device with measurements of inlet and outlet
temperature of latent heat storage device filled with PCM . In such a
system some design factors are important for the performance of the system
. Design factor can be for example fins on heat storage device. A
comparison was made between a flat heat storage device and a heat storage
device with fins. It turned out that in the heat storage with fins PCM melting time was reduced .
Much interest in the last ten years was also attracted by sorption and thermochemical heat storage devices. In this area some project concerning absorption and adsorption heat storage devices are carried out. Their use is limited due to high prices of materials. The advantage of this technology is the possibility of long-term heat storage .
Description of the system
Solar radiation is a sustainable source of energy. The annual amount of solar energy that falls on Earth is more than eight thousand times larger than the annual global demand for primary energy.
Local distribution of the total annual amount of solar energy is determined by climatic and meteorological factors that are highly dependent on their location.
For exploitation of solar energy a system composed of solar energy collector, low-temperature (latent) heat storage device, heat pump and heating system, which is linked to heat storage device, can be used. System is presented in Figure 1.
Figure 1. Scheme of the heating system.
Functioning of the system
collector absorbs solar energy, which is then transmitted by the heat exchanger
to the latent heat storage device, which is filled with a phase changing
material (PCM) - paraffin. The phase change material store energy in the
process of changing in their physical state from solid to liquid. In our case
the melting temperature was 30°C.
Thermal energy is then used by the heat pump from the latent heat storage device to a higher temperature level. This energy is stored in heat storage device and then sent through a heat exchanger into the heating system which is used for heating of building. In this way a space temperature of 20°C can be provided. The temperature of the heating system is 40°C.
In analysis of complex heating system a computer program - application that allowed simulation of behaviour of the heating system in different climatic conditions was used. To implement the simulation input data were: hourly solar radiation, the corresponding external temperature, characteristics of the solar energy collector, latent heat storage device filled with paraffin Rubitherm RT 31, heat pump characteristic and low-energy house characteristic. For weather data Test Reference Year (TRY) was used.
The calculation scheme is presented in Figure 2.
Figure 2. Scheme of the calculation.
following are the physical parameters of the system components:
energy collector - (SC).
energy collector is designed to convert solar energy into heat. In analysed
system two solar collectors were used. The characteristic of each collector is
presented in Table 1.
Table 1. Characteristic of the solar collector.
The amount of heat generated by the sun is calculated using Equation 1.
QSC = F´ × ASC × [Gglob.b × tcover × aabs – kUSC × (Tmid – Tamb) (1)
Dimensionless efficiency factor of the absorber
ASSE Solar energy collector area (m²)
Gglob.b Global solar radiation in the plane of the
collector cover (W/m²)
tcover Transitivity of the solar energy collector cover
aabs Absorptivity of solar radiation on the absorber
USC Thermal conductivity of the solar collector (W/m²K)
Tmid Mean temperature of the liquid in the collector (K)
Tamb Ambient temperature (K)
Latent heat storage (LHS) with paraffin Rubitherm RT 31
storage at low temperature level, we have used latent heat storage with
paraffin Rubitherm RT 31 with following characteristics:
Table 2. Characteristic of paraffin RT 31.
T melting point
that paraffin have is that they store a greater amount of energy without
changing their temperature at phase change (solid - liquid and vice versa) as
shown in Figure 3. In this case the temperature at which
the phase change occurs was 31°C.
Figure 3. Temperature distribution in the latent heat storage device with RT 31.
Heat pump (HP)
The role of heat pump in the heating system is to raise the thermal energy from a lower temperature level to a higher temperature level. COP (coefficient of performance) of heat pumps have been calculated using Equation 2 for each heat source temperature according to Figure 4 for the output temperature of the heating system (water flow) of 40°C. The temperature of the stored heat source in a latent heat storage device has varied depending on solar gains.
Figure 4. Diagram for determining COP.
COPheating Coefficient of performance for heating
Qc Heat from a heat source (kWh)
WHP Heat pump supplied energy (kWh)
Low energy building
The installed system was used for heating of low energy building with the following characteristics:
Calculation of the losses has been made by the Equation 3.
Qloss = A × U × (Ti – Te) (3)
Qloss Heat losses (kWh)
A Building envelope area (m²)
U Overall thermal transmittance of building (W/m²K)
Ti Internal temperature (K)
Te External temperature (K)
At a time when the sun was not able to provide sufficient thermal energy secondary heating system is switched on. In this case the biomass boiler.
Results and analysis
Analysis of a complex heating system has been conducted for a period of heating season, which we define as the period between October and March. Data on climatic conditions have been obtained for the cities: Rome, Ljubljana, London and Stockholm.
The analysis showed that the maximum solar
gains through the entire heating season are highest in Rome, the lowest in
Stockholm, where during the months November, December and January they are
almost zero. Most solar gains for all cities are obtained in March (Figure 5).
Figure 5. Solar gains during the heating season - QSC.
Heat losses in the heating season are the largest in Stockholm, and the smallest in Rome. For all the considered sites maximal losses are in January (Figure 6).
Figure 6. Heat losses during the heating season for the concerned city – Qloss.
Figure 7 presents data of heat obtained with a heat pump by month during the heating season. From the diagram we can see that it is possible to get more heat in March. This fact is linked to a sufficient amount of sun energy during this month.
In given location the maximum possible average gain of heat for heating is in Rome. Maximum heat gain can be achieved in Ljubljana in March, but the lowest results are in Stockholm in November, December and January.
Figure 7. Heating with a heat pump in the heating season for the concerned city – QHP.
Efficiency of the heat pump or coefficient of performance (COP) gives us the ratio between produced heat and input energy (electricity). In the presented system COP reached values during the heating season between 0 and 5.69. Value of 0 means that there was no heat source from which heat pump could draw the heat, and raises it at a higher temperature level.
As presented in Figure 8,
the value 0 was reached in Stockholm in December and January. The maximum value
of COP is 5.69, which was reached in Rome, Ljubljana and London. In Rome this
value was reached in the months October, November, February and March, in
Ljubljana in October and March and in London in the months of October and
March. In Stockholm, the maximum value of COP was 5.12.
Figure 8. Maximum COP values during the heating season.
Because through the all heating season there is not enough sun for heating and in consequence reheating is needed. As a secondary source of heat biomass has been chosen. As shown in Figure 9 the greatest need for the latter is in Stockholm. It is necessary through all the heating season. In Ljubljana, reheating is not required in the month of October, the highest value is reached in Stockholm in January. Through the heating season, the reheating is necessary at lower rates in Rome.
Figure 9. Additional heating with biomass in the heating season forthe concerned city.
Because of unsustainable use of organic fossil fuels on which the energy supply of mankind relies, it is necessary to introduce advanced technologies for heating. Among the environmentally friendly technologies that are used for heating solar energy is one of them. Solar energy in combination with a heat pump and a latent heat storage device represents an economical and efficient heating system.
To the economy of this system contributes its geographical position in first place because of the following reason: more we move towards the equator, more solar energy is available and vice versa. When solar energy does not provide sufficient thermal energy to cover losses of the building we need reheating. In this case the heating system becomes less economical, since reheating is payable and solar energy is free of charge. With this kind of system one can use solar energy to provide approximately 50% of the annual heat requirements for a low energy house. The amount of sun also has an impact on the coefficient of performance (COP) of heat pump. In accordance with the geographical position the latter can reach a value of nearly 6.
 Directive 2010/31/EU of the European Parliament and of the Council of 19 May 2010 on the energy performance of buildings (http://eur-lex.europa.eu/).
 U. Stritih, V.Butala, Optimization of a thermal storage unit combined with a biomass boiler for heating buildings, Renewable Energy 29 (2004) 2011-2022.
Badescu, Model of a thermal energy storage device integrated into a solar
assisted heat pump system for heating, Energy Conversion and Management 44
Lin, Lin-jye Chun, Wen-Shing Lee, Sih-Li Chen, Thermal performance of a
two-phase thermo syphon energy storage system, Solar energy 75 (2003) 295-306.
 Vincent Veer Tyagi, D. Buddhi, PCM thermal storage in buildings: A state of art, Renewable and Sustainable Energy Reviews 11 (2007) 1146-1166.
 Murat Kenisarin, Khamid Mahkamov, Solar energy storage using phase change materials, Renewable and Sustainable Energy Reviews 11 (2007) 1913-1965.
 Yinping Zhang, Goubing Zhou, Kunping Lin, Qunli Zhang, Hongfa Di, Application of latent heat thermal energy storage in buildings: State-of-art and outlook, Building and Environment 42 (2006) 2197-2209.
Zalba, Jose M. Martin, Luisa F. Cabeza, Herald Mehling, Review on thermal
energy storage with phase change: materials, heat transfer analysis and
application, Applied Thermal Engineering 23 (2003) 251-283.
Akgun, Orhan Aydin, Kamil Kajgusuz, Thermal energy storage performance of
paraffin in a novel tube–in-shell system, Applied Thermal Engineering 28 (2008)
Felix Regin, S. C. Solanki, J. S. Sami, Latent heat thermal energy storage
using cylindrical capsule: Numerical and experimental investigations, Renewable
Energy 31 (2006) 2025-2041.
 M. Esen, Thermal performance of a solar-aided latent heat store used for space heating by heat pump, Solar Energy 69 (2000) 15-25.
 Omer Comakli, Mahmut Bayramoslu, Kamil Kajgusuz, A thermodynamic model of a solar assisted heat pump system with energy storage, Solar Energy 56 (1996) 485-492.
 U. Stritih, An experimental study of enhanced heat transfer in rectangular PCM thermal storage, International Journal of Heat and Mass Transfer 47 (2004) 2841-2847.
 K. Edem N'Tsoukpoc, Hui Liu, Nolwenn Le Pierres in Lingai Luo, A review on long-term sorption solar energy storage, Renewable and Sustainable Energy Reviews 13 (2009) 2385-2396.